Passive fire protection is a life safety system and as such should be designed in a compliant manner. It is important for structural and fire engineers to understand the compliance requirements of each fire protection system so that appropriate measures can be enforced into their design. For instance, structural engineers are required to specify the limiting steel temperatures required for steel elements to ensure structural adequacy can be maintained. Fire engineers may also be required to ensure the adequate FRL has been achieved with the fire safety systems specified in a project. Discussing the issues of compliance ahead of time with Permax can assist throughout any project life cycle.
Here is how we can help you throughout the time line of your project:
- Obtain limiting steel temperatures and ensure all specified steel can achieve required FRL
- Review design details of intumescent coated members to ensure appropriate expansion and heat transfer principles are designed for
- Provide advice on where more than one passive fire protection system is used on a design
- Steel schedule is developed by the Permax technical team with intumescent DFT loadings across the project
- One of the Permax approved applicators can provide a tender quote based on the product and application cost.
- Ensure passive fire protection installers are aware of the compliance and specific fire rating requirements, for instance coat back and direct fixings.
FREQUENTLY ASKED QUESTIONS
Hp/A, is a method of calculating the steel section factor. It is the heated perimeter to cross sectional area ratio of a steel member. Hp/A gives an indication of the steel heating rate and governs selection of steel sections that can achieve the required FRL. Generally, a larger, thicker steel member will have a lower Hp/A and thus have a lower heating rate than a smaller, thinner steel member. This is important to consider because members with high Hp/A will require more passive fire protection than members with low Hp/A.
When limiting steel temperatures are not provided for structural steel work, the standard limiting steel temperatures of 550ᵒC or 620ᵒC are used as default. It is important to ensure structural steel limiting steel temperatures are confirmed with the project structural engineer.
Limiting steel temperature, also known as the critical steel temperature is the temperature which a structural member must be prevented from reaching, in order to retain its required strength capacity. Limiting steel temperatures can be calculated as per AS4100 cl 12.5.
The structural loading case used in a fire case can be determined in AS1170.0. It is different from the ultimate load case structural loading. For example, the ultimate limit state loading for beams is 1.25G + 1.5Q, where G is the designed dead load, and Q is the designed live load. Under a fire load case the design load which structural engineers determine is G + Ψc Q. Where Ψc is the combination factor determined by the use of the building.
Load ratio, rf, is calculated based on the design load under a fire load case over the design member capacity at room temperature. The load ratio determines the limiting steel temperature as per clause 12.5 in AS4100.1998 – Section 12 Tl= 905 – 690rf where Tl is the limiting steel temperature.
For example, a 460UB67.1 beam with 399kNm design flexural strength capacity at room temperature and 130kNm design bending moment in a fire environment will have a load ratio of approximately Rf = 0.33.
Core-filling is the process of adding a grout or concrete mixture of 40MPa or less to a hollow structural steel section to create a composite column. The purpose of core-filling is to reduce the section factor of the structural steel, allowing it to achieve a higher FRL rating with a thinner coat of intumescent.
Connections are usually fire-rated to the same dry film thickness of the primary member directly attached. Connections are usually masked during off-site spraying, and are sprayed on-site after the steel is erected. Permax have pre-formed intumescent bolt caps that can also be used to fire rate steel bolts.
There are many possible configurations of plasterboard sheeting used in conjunction with Nullifire SC902 coated steelwork. Please contact Permax for detail specific advice.
Coat-back is a process of coating an area beyond the specified protected structural steel member. It can be required when fire protected steel is connected to steel which is not fire protected. In this case it is recommended 500mm coat-back is provided to the non- fire rated element to prevent heat transfer to the member which requires fire protection. Follow this link to read more about coat-back in an advisory note. Link?
Get in Touch
Speak to the leaders in passive fire protection
The Difference Between Engineers and Fire Engineers
Fun fact for your next trivia night: the term “engineer” derives from Medieval Latin and the word “ingeniare”, which means to design or devise. Ever since the wheel was invented (and even before that), humans have been devising clever inventions, designed to astound, improve, or carry out a function that too often we all take […]
Is the steel section big enough to achieve the proposed FRL without utilizing any fire protection?
When it comes to new building construction, there is a predominant focus on keeping construction costs as low as possible while still satisfying the performance requirements in the building codes. Regarding fire rating, we are often asked whether the structural steel section is sufficient in achieving the proposed Fire Resistance Level (FRL) without using any fire […]
The relationship between fire upgrade orders and fire rating
When your building is considered by your local council as unsafe when it comes to fire safety, you or your acting strata manager will receive fire safety upgrade orders. A required completion date is set in the order, and thus, you’ll need to install the necessary upgrade such as a door with the appropriate fire […]
You are about to download a file from the Permax site. Please note All technical advisory notes generated by Permax are based on research papers, indicative fire tests and any other existing evidence. These documents should not be used as an official evidence as design engineers should review the information and determine the reliability of the documents.
Permax constantly update the documentations based on the new fire testing outcomes and change of standards and regulations. To ensure the documents you read are up-to-date, please contact the Permax technical team.